UL 87:2019-09 Power-Operated Dispensing Devices for Petroleum Products.
1.1 These requirements apply to power-operated dispensing devices for petroleum products such as gasoline for use as motor fuel. Requirements for the installation and use of these dispensing devices are included in the Automotive and Marine Service Station Code, NFPA 30A, and the National Electrical Code, NFPA 70.
1.2 These requirements apply to wiring methods used to install or interconnect such control equipment when the equipment is located directly on or within the housing of the dispensing device. These requirements do not apply to control equipment that may authorize, monitor, or interrupt operation of a power-operated dispensing device. Such equipment includes panel mounted equipment located adjacent to the dispensing device, remote consoles located inside a permanent structure, and auxiliary equipment physically attached to the dispensing device or enclosed by the pedestal and housing.
2.1.1 Except as indicated in 2.1.2, a component of a product covered by this standard shall comply with the requirements for that component. See Appendix A for a list of typical standards covering components used in the products covered by this standard.
2.1.2 A component is not required to comply with a specific requirement that:
a) Involves a feature or characteristic not required in the application of the component in the product covered by this standard, or
b) Is superseded by a requirement in this standard.
2.1.3 A component shall be used in accordance with its rating established for the intended conditions of use.
2.1.4 Specific components are incomplete in construction features or restricted in performance capabilities. Such components are intended for use only under limited conditions, such as certain temperatures not exceeding specified limits, and shall be used only under those specific conditions.UL 87 pdf download.