NFPA 30B-2019 Code for the Manufacture and Storage of Aerosol Products.
4.4 Heating Equipment. Heating equipment shall be installed in accordance with the applicable requirements of the follow‐ ing: (1) NFPA 31, Standard for the Installation of Oil-Burning Equip‐ ment (2) NFPA 54, National Fuel Gas Code (3) NFPA 58, Liquefed Petroleum Gas Code (4) NFPA 85, Boiler and Combustion Systems Hazards Code 4.5 Flammable Liquids and Gases. Areas in which fammable liquids and fammable gases are handled or stored shall meet the applicable requirements of the following: (1) NFPA 30, Flammable and Combustible Liquids Code (2) NFPA 58, Liquefed Petroleum Gas Code 4.6 Fire Protection. Δ 4.6.1 Automatic Sprinkler Protection. Installations of auto‐ matic sprinklers, where required by this code, shall be installed in accordance with NFPA 13 and the provisions of this code. Δ 18.104.22.168 Where the provisions of this code and NFPA 13 differ, the provisions of this code shall prevail. Δ 22.214.171.124 Where this code does not address specifc automatic sprinkler protection criteria, the provisions of NFPA 13 shall prevail. 4.6.2 Standpipe and Hose System. Installations of standpipe and hose systems, where required by this code, shall be designed and installed in accordance with NFPA 14 and with the provisions of this code. Only combination or spray hose nozzles shall be used. Δ 4.6.3 Portable Fire Extinguishers. Fire extinguishers shall be provided in accordance with NFPA 10.
126.96.36.199 Defagration vents shall relieve to a safe location to avoid injury to personnel and to minimize property damage. Δ 188.8.131.52 Defagration venting shall be designed and installed in accordance with NFPA 68. Δ 184.108.40.206 In existing rooms where defagration venting cannot be installed, a defagration suppression system that meets the requirements of NFPA 69 shall be installed. 220.127.116.11 Defagration vents shall be maintained in accordance with 8.6.3. 5.4 Ventilation. 5.4.1* Mechanical exhaust ventilation shall be provided for fammable concentrate–flling areas and for fammable propel‐ lant charging and pump rooms in accordance with 5.4.2 or 5.4.3, as applicable. 18.104.22.168 Ventilation systems shall include exhaust systems and make-up air systems.NFPA 30B pdf download.