NFPA 220-2018 Standard on Types of Building Construction.
5.1.10 Structural elements within exterior walls or located along the exterior perimeter of a building or structure shall have a fre resistance rating as required by Table 4.1.1 for exte‐ rior bearing walls based on the type of construction. [5000:22.214.171.124] 5.1.11* Structural elements within an exterior wall located where openings are not permitted, or where protection of openings is required in accordance with 7.3.5 of NFPA 5000, shall have a fre resistance rating based on protection against exterior fre exposure as required for exterior bearing walls or the structural element, whichever requires the greater fre resistance rating. [5000:126.96.36.199] 5.1.12 The edges of lugs, brackets, rivets, and bolt heads attached to structural elements shall be permitted to extend to within 1 in. (25 mm) of the surface of the fre-resistive protec‐ tion. [5000:188.8.131.52] 5.1.13 Conduits, pipes, or ducts shall not be embedded within the required fre-resistive protection of any structural elements requiring individual encasement to achieve the required fre resistance rating. [5000:184.108.40.206] 5.1.14 Fire-resistive materials covering columns required to have a fre resistance rating, where exposed to impact damage by moving vehicles, by handling of merchandise, or by other means, shall be protected from damage. [5000:220.127.116.11] 5.1.15 In load bearing, light frame walls requiring a fre resist‐ ance rating, membrane protection shall not be required to extend beyond the edge or fange of the construction in open‐ ings that are framed or where doors or windows are installed. [5000:18.104.22.168]
A.3.2.2 Authority Having Jurisdiction (AHJ). The phrase “authority having jurisdiction,” or its acronym AHJ, is used in NFPA documents in a broad manner, since jurisdictions and approval agencies vary, as do their responsibilities. Where public safety is primary, the authority having jurisdiction may be a federal, state, local, or other regional department or indi‐ vidual such as a fre chief; fre marshal; chief of a fre preven‐ tion bureau, labor department, or health department; building offcial; electrical inspector; or others having statutory author‐ ity. For insurance purposes, an insurance inspection depart‐ ment, rating bureau, or other insurance company representative may be the authority having jurisdiction. In many circumstances, the property owner or his or her designa‐ ted agent assumes the role of the authority having jurisdiction; at government installations, the commanding offcer or depart‐ mental offcial may be the authority having jurisdiction. A.3.2.3 Listed. The means for identifying listed equipment may vary for each organization concerned with product evalua‐ tion; some organizations do not recognize equipment as listed unless it is also labeled. The authority having jurisdiction should utilize the system employed by the listing organization to identify a listed product.
NFPA 220 pdf download.